Fireproofing paints are gradually becoming more and more widespread. Their use is actually quite beneficial, as these materials are capable to solve several major problems, including the main – protection of material from the fire.
|№||Name of parameters||The value|
|1||The consistency and appearance of the composition||White suspension|
|2||Appearance of coating in liquid form||White homogeneous mass|
|Appearance of coating in dry form||White homogeneous coating|
|7||Consumption of coatings kilogram/m2 (excluding technical losses)|
· metal (fireprection up to 45 min)
· metal (fireprection up to 60 min)
· 2.1 with dry layer thickness 1.4 mm
· 2.2 with dry layer thickness 2.8 mm
· 1.2 with dry layer thickness 1.0 mm
|8||Mass fraction of nonvolatile substances, nor less,%||60|
|9||Viscosity by VZ-246 (RUS "ВЗ-246"), nor less, sec||45|
|10||Drying time at 20 °C (up to the grade 3)||24 hours|
|12||Density of coating in liquid form at 20 ° C, kg/m3||1250|
|13||Density of coating in dry form at 20 ° C, kg/m3||1000|
|14||Useful life of the coating||nor less 10 years|
|15||Flammability class||Poorly burns or does not burn|
|16||Ignition class||Does not ignite|
|17||Flame spread over the surface||Does not spread flame on the surface|
|18||Smoke-forming ability||Moderate smoke generation|
|19||The toxicity of combustion products||Moderately dangerous|
a) Water pipes
b) Oil pipes
c) Gas pipes
a) Air transport
b) Ground transport
c) Sea transport
3) Non-residential building
a) Refrigerator rooms
b) Thermal, nuclear, hydro power plants
c) Warehouses, hangars, garages
d) Industrial buildings
1) Gas and oil industry
2) Steel mills
3) Food processing industry
4) Residential buildings
e) Elevators and elevator shafts
f) Stairs and stair openings
5) Shipping containers
a) Metal containers
b) Cryogenic containers (medicine)
c) Thermo bags
a) For fire-fighters
b) For the steel mill workers
7) Incubators and climate system
8) Sports complexes, stadiums
9) Monuments of architecture
10) Tanks, gas, oil storage
1. Instructions for use.
1.1. Preparation of the coating.
Any coating of SPA Zelenopol is supplied ready for use.
Before applying the coating it must be mixed with a hand mixer (drill is not preferable) to obtain homogeneous mass, with a mandatory immersion of nozzle down to the bottom of the bucket.
Do not use high speed while stirring the coating!
1.2 The order of coating application to metal, concrete, brick, wood and other surfaces.
Preparation of metal surface for application.
- thoroughly clean the surface from rust;
- if necessary treat the surface with rust converter;
- dry the treated surfaces;
- cover the metal surface with a thin layer of anticorrosion primer brand GF-021. The thickness of the layer should be not less than 50 microns, the drying time 72 hours.
Preparation of concrete, brick, wood and other surfaces for application.
- thoroughly clean the surfaces: remove loose parts, cracks, oily inclusion and gloss.
- apply 1 or 2 coats of deep soaking primer;
- dry the treated surfaces.
The technological process of coating application on metal, concrete, brick, wood and other surfaces.
Apply the coating with a thin layer on prepared surface covered with primer (thickness should not exceed 400 micrometers). Apply the paint with a soft brush with a long nap or airless spray (devices like «Vagner»). Dry for 24 hours at a temperature of 20 ° C and humidity no more than 85%.
In case of brushing, the brush should be preliminary dipped in *solvent during the application process.
The paint must be under constant stirring during application process, so that the fluid is not collected at the bottom of the container.
The following layers (of thickness no more than0 500 microns) must be applied under normal conditions after drying of the previous layer to form the required coating thickness. The drying time is 24 hours at a temperature of 20 ° C, humidity no more than 85%.
Upon agreement with manufacturer, the coating can also be applied on a heated surfaces (up to 150° C).
In this case the thickness of each of the first three layers should not exceed 50 microns, and each layer must be dried for at least two hours. A *solvent must be added to the coating to achieve this.
The amount of *solvent depends on the object surface temperature and the ambient temperature.
After coating application, brushes and other equipment must be thoroughly washed in *solvents.
2. Manufacturer warranty.
The manufacturer guarantees the compliance of the coating with specification requirements. Subject to the conditions of transportation and storage, the warranty period of coating storage is 12 months from the date of manufacture.
Beyond the warranty period of storage, the coating is subject to re-examination for compliance with specifications. Upon receipt of positive results the coating can be used for the intended purposes.
3. Storage conditions.
Store the coating in tightly closed containers at a temperature:
- from -30 ° C to +35 ° C for solvent-based coating
- from +5 ° C to +35 ° C for water-based coating.
- if the coating is solvent based it may be diluted with xylene or butyl acetate;
- If the coating is water-based it may be diluted with water only.